Hydronic boilers operate in the pressure range between 10 and 30 psi. Water feed to the piping network goes through a separate pressure reducing valve (boiler feed regulator) that regulates below system static pressure. 12 psi is a standard setting for the boiler feeds. If the boiler loses water due to small leaks/evaporation the boiler feed will open to supply make-up water. Unless the equipment has been drained for servicing, this typical make up flow event is low flow rate and low volume. The condition described may show up as an intermittent/periodic low flow event below .5 gpm. It may also be captured during a Health Check. Therefore, the call for water at 12 psi may cause a small drip to be detected, however, it is unlikely that the small drip would be alerted on a consistent basis.
Articles in this section
- How will this system react to recirculation tanks in on demand hot water heater’s?
- What sizes do they come in, can they be used in commercial applications and farm wells?
- Is this a product that we can tie into one of our offices to monitor water for people that do not have skills to run the apps?
- How does it work with condensation can It detect a difference?
- Is there a warranty if we install this product on well water or city?
- How does the system react to hydronic boiler systems when they call for water at 12 psi?
- Does this product shut down automatically?
- How does it respond to hot water recirculation loops in the plumbing system?
- How does this product hold up to well water / hard water?
- Does this product reduce the flow of water?