Hydronic boilers operate in the pressure range between 10 and 30 psi. Water feed to the piping network goes through a separate pressure reducing valve (boiler feed regulator) that regulates below system static pressure. 12 psi is a standard setting for the boiler feeds. If the boiler loses water due to small leaks/evaporation the boiler feed will open to supply make-up water. Unless the equipment has been drained for servicing, this typical make up flow event is low flow rate and low volume. The condition described may show up as an intermittent/periodic low flow event below .5 gpm. It may also be captured during a Health Check. Therefore, the call for water at 12 psi may cause a small drip to be detected, however, it is unlikely that the small drip would be alerted on a consistent basis.
Articles in this section
- How do I turn on / off my water through the Flo by Moen App?
- How do I replace my Flo by Moen device?
- Enabling TCP Ports for wireless routers to pair your Flo by Moen device.
- How does the Flo by Moen device measure flow rate? Temperature gradient?
- How does the Flo by Moen device categorize a catastrophic leak which shuts off water?
- How does Flo's machine learning software handle reverse osmosis systems?
- Proper grounding for installations
- How will this system react to recirculation tanks in on demand water heater’s?
- What size does the Flo by Moen device come in, can it be used in commercial applications and farm wells?
- Is this a product that we can tie into one of our offices to monitor water for people that do not have skills to run the apps?