The Flo by Moen device is to be installed on the homes main water supply line just after the existing shut off valve and pressure reducing valve.* The device should be installed before the plumbing system branches off into the different fixtures in the home.
DO NOT install Flo by Moen device on fire sprinkler or suppression systems and hot water distribution lines.
*NOTE: Some homes may not have a Pressure Reducing Valve "PRV." Please check with local plumbing codes if installing a PRV is needed.
In some cases where space is limited on the homes water line, the installation may need to be reconfigured to properly install the Flo by Moen device. Additional piping, bent connectors (“elbows”) and fittings can be added to create the proper installation.**
**NOTE: THE Flo by Moen device can be installed in a vertical or horizontal position.
Once the device is installed, connect the AC power adaptor to a nearby outlet to power the Flo by Moen device and verify that the device is connected to the homes WIFI network before restoring water supply to the home. The "Status" LED should be solid green indicating a successful internet connection is established. ***
***NOTE: Remember to download the Flo by Moen App and "PAIR" your Flo by Moen device before installation.
If you need assistance please contact us.